Due to extreme cold I had to replace main water line. While at it I replaced new 40/60 pressure switch and pressure gauge. Pressure switch will not cut in or off and well pump is constantly running. I am unsure if if I wired the switch backwards or not. I have the breaker running to the center two poles and the pump running to the outer two poles. Is this correct?