# Sizing of tankless few questions.

Discussion in 'Tankless Water Heater Forum' started by C Wolford, Sep 4, 2019.

1. ### C WolfordNew Member

Joined:
Jan 23, 2019
Location:
IL
I am on city water. treatment plant is 7 miles away.

1st when I was looking in to this last year, I found at winter my TAP water was coming in at 36-46 cant remember. Not sure if there water treatment company would have a log. The thing is on all the ground water maps I am close to the line of 57/52. Is this normal? All i know is i recall a 10-20 lower temp from the ground water chart.

2nd. I have a 1 bath, 4 person home. wife like to get the Washing Machine, and dishwasher going at the same time maybe a bath/shower. so I should account for the max flow of all this for hot water demand?

3rd. Bath tub filling. I know the valves mix cold with hot, but from my understanding all the charts they give have these water heater set to 105 F. That would require straight hot to fill the tub right? So to get a true flow rate need for the tub I need to find the mixing % with cold at a give delta T right? The short of #3 is I do need to have a higher water temp than the 105 f most manufacturers use to rate there flow rate with. correct?

4th Am I crazy and over thinking here or am I on the right track?

Joined:
Jan 14, 2009
Location:
01609
You're overthinking this, but do the math if you want. For incoming water temps of 40F you'll definitely want a 199,000 BTU/hr condensing tankless (if tankless).

No matter how high you raise it and mix it down, the limitations are the max burner output and the temperature difference between what's coming in the cold mains and what's going out the tap. For a tub fill 110F is more realistic, for a shower 105F is fair. At 40F incoming that's a 70F or 65F temperature rise.

Every gallon per minute (gpm) is very close to 500 lbs per hour. It takes 1 BTU to raise a pound of water 1 degree F. The max output of a 199K tankless is about 190,000 BTU/hr (in your dreams- in practice it's slightly less.)

So for a 70F bathtub fill your max fill rate is 190,000/70F=~2700 lbs/hr. Translating that to gpm would be 2700/500= 5.4 gpm

That's not crazy slow, but it's not super-fast either, and if sharing the burner with other hot water draws it'll take longer.

A 2.5 gpm shower with a 65F temperture rise takes 2.5 x 500lbs/hr x 65F= 81,250 BTU/hr, which is nearly half the max output of a 199K tankless, and that's OK- it's enough to allow somebody to run the washing machine or run a tap at the kitchen sink without hearing screaming coming from the shower, or even have a second shower running, but not enough to fill a tub at a reasonable rate while someone is showering in the other bathroom (that you don't have).

With a single bathroom you could cut back on that burner sizing a bit if you don't mind slower tub fills A typical bathtub takes ~35 gallons, so with a 199K tankless it'll take 6 minutes, but it starts to stretch out if dropping back to 150K burner, and takes a LOT longer with a 120K burner.

4. ### C WolfordNew Member

Joined:
Jan 23, 2019
Location:
IL
Thats what I was afraid of. Seems I got some more reading to do pro vs cons of tank to tankless. I wanted the nice endless hot, on demand, savings etc... but it seems it needs a huge one to do a small 4 person house at least in the winter when the temps are down.

Thanks for the time and for responding.

Joined:
Jan 14, 2009
Location:
01609
If it's showering performance you're after and have another grand to spend, a drainwater heat recovery heat exchanger that's 50% efficiency or higher under NRCan testing protocols can allow down-sizing the tankless. In showering mode it's effectively using half the amount of burner capacity that it would take to run the shower without it. The current state of the art is EcoDrain's V1000 series, but I'm still pretty happy with the 4" x 48" Renewability PowerPipe I installed about a decade ago.

It does nothing for tub filling performance, or batch draws from washers, etc, but it doubles the showering capacity without using more fuel by just keeping a large fraction of the heat from going literally down the drain.

With expensive fuels such as LP or plain old electric tank the "payback" is pretty short on fuel savings if four people are showering daily.