|Posted by LonnythePlumber on June 30, 2004 at 21:16:42:|
|In response to Re: plumbing|
: can you drain a water heater pan into a drain line or do you have to run it by itself to the outside.
"2000 UPC 510.7 ...to an approved location." This would be an indirect connection with air gap into an open receptor like a floor drain. Some jurisdictions allow sump pump basins. LonnythePlumber
|Replies to this post|
|There are none.|