|Posted by jimbo on May 07, 2004 at 22:24:44:|
|In response to Re: moving water heater|
: First, the PB. I don't think this is allowed by code anywhere anymore. Hot chlorinated water eats PB.
You say that attic location is common. Maybe so. But if you figure a pad of say 2x2 feet, that's 4 sqft. 450 / 4 = 112 pound per square foot floor load. I doubt if your ceiling joists are sized to support this.
A gas water heater brings up the whole subject of combustion air supply. You need a city inspector to tell you what they would require up there.
|Replies to this post|
|There are none.|