|Posted by hj on May 06, 2004 at 10:07:14:|
|In response to Re: pvc fittings|
A sanitary tee can almost never be installed in a horizontal waste line, and you have to use a "Y", or combination Y-1/8 bend fitting. In a vertical line, a tee can be used, and in most cases you can also use a combo, but there are some situations where the combination fitting is not allowed in a verical line. So the specific application determines whether you have to have one or the other, or if they are interchangeable.
: Any difference in application between wye's and sanitary drain T's. Ie. 4x4x2 wye vs. 4x4x1 1/2 sanitary (red)?
|Replies to this post|
|There are none.|