|Posted by hj on March 27, 2004 at 21:55:26:|
|In response to Re: Need help on water heater|
Unless the original vent pipe was oversized, it is not large enough for two heaters. It could be a lack of gas, but only a professional can tell by checking the consumption when both heaters are operating and the pressure at the heaters at that time.
: I told the other plumber about my gas.
: I just put in a t on the (vent pipe) and tied in the new pipe. I used screws on the joints.
: How do I check the for enough gas?
: Thanks for helping me
|Replies to this post|
|There are none.|