|Posted by hj on March 02, 2004 at 22:02:47:|
|In response to Re: does this DWV layout look legal?|
A 3x2 Y, facing towards the lavatory location, in the vertical pipe with the vent then sloping upward with the lavatory connected to it would satisfy the code requirement. If I were doing it, the 3" riser would be at the lavatory location with the toilet connected to a sanitary tee rotated to the proper orientation to extend to the toilet location. Then a proper cleanout tee above the floor with a reducer and a 2x1 1/2" tee for the lavatory.
: can the tub vent go horizontal before it goes up for the vent?
: where the lav and tub tie into toilet line is the use of a Y + a 45 correct? it is horizontal to horizontal.
|Replies to this post|
|There are none.|