|Posted by e-plumber on December 28, 2003 at 15:06:12:|
|In response to Re: Air in the baseboards!!!!|
: I have already seen the past posting on this subject, but I have something to add to it.
: There is an American system setup at the boiler and I don't know if it is working properly. (Most likely not since there is air in the lines.)There is an eX-Trol tank with a 71 valve assembly, and above it is a Series 700 float type air vent. At the top of the air vent is a Schrader valve with a cap twisted on it. Should this system remove the air automatically, or do I need to bleed it with the Schrader valve manually? The coldest time of the year is upon me, and I need to make sure the system is up and running properly. We have already had the core checked by a professional, and it is fine. Any Help?
|Replies to this post|
|There are none.|