|Posted by Hube on December 13, 2003 at 07:46:40:|
|In response to Re: low water volume|
: : : I am having a problem with very low water volume is more than one faucet is opened the second has hardley any flow at all.
: : : My pressure switch is set to a cut on at approximately 30 lbs and off at aproximately 50 pounds of pressure. My pump is a 3/4 hp submersible at approximately 140 feet and the static water level in the well is approximately 30 feet.
: : : I have a 2 story house and there is little difference on the secod floor. Any ideas?
: : : also should the air pressure in the tank be set with the tank empty or at pressure?
: : The air should be set with the tank EMPTY and all taps closed off. Set psi 2 lbs. below the cut-in setting .(a bicycle pump will do).. You can adjust the pressure switch to be a little higher (35-55) and see if that will help. But FIRST, try the existing settings once you have put the proper air in the tank. If you don't know HOW to increase the switch to the new settings, post back with the type and model of switch. Hube
|Replies to this post|
|There are none.|