|Posted by Hube on December 02, 2003 at 09:56:49:|
|In response to Re: correct switch for shallow pump|
: we have a 1/2 hp shallow well jet pump. The problem we are having is that the pressure starts out fine and quicky drops off to almost nothing. We did the draw off calculation and we got 1.76 gpm. Our landlord says that we can't expect more from a shallow well. Is this true?
: What are the correct cut in/cut out pressures for a shallow well? We are cuurently 40/60 with a 40/60 switch, before it was 20/40 on the same 40/60 switch.
: What our landlord said is that the pump is pulling too hard and then it can't catch up to keep up the water pressure and that this will be fixed by putting a 20/40 switch, but won't this just lower the overall pressure?
: Lee Brown
; What size PRESSURE TANK is associated with this Jet Pump? A tanks size will govern the amount of water you will "store" in a complete on/off cycle of the pump. A setting of 20/40 will give you more water than a 30/50 setting (approx 20 % more. Post back with info and we wil advise further, Hube
|Replies to this post|
|There are none.|