|Posted by Ron Lee on January 22, 2003 at 20:11:06:|
|In response to Re: pipe size|
: You have to know the total length of the pipe system and then the various sizes can be calculated depending on the load at each connection.
: : Is there a chart available to calculate the pipe size needed to carry 300000 btu's of natural gas to my furnace, dryer, stove, fireplace etc.
hj I know that a 3/4 inch iron pipe will carry 300000 btu's of LP-Gas vapor for 52 ft at 11 inch wc. What size pipe will it take to carry 300000 btu's of natural gas vapor the same distance between low pressure reg and appliance.
|Replies to this post|
|There are none.|