|Posted by hj on January 14, 2003 at 08:05:54:|
|In response to Re: Water pressure regulator question|
It means that the regulator is not maintaining its setting when there is not flow, for some reason. You can rebuild it if you can find the repair kit. My time is too valuable to try repairing them since the valve could still malfunction. Therefore, I always replace them when that happens. The idea of a PRV is to not subject the system to the high line pressures. If the valve does not hold in a static condition, then the system is still under the higher pressure, regardless of whether the valve maintains a proper dynamic pressure.
: : The regulator is "slipping".
: What does that exactly mean? In that case would I need to rebuild the regulator, or just take it apart and clean it? It's a Wilkins model 70.