|Posted by Andrew on December 17, 2002 at 16:05:28:|
|In response to Re: Vibrating pipes|
: Sounds like you have an airlock or a valve seal that is not seating correctly, airlocks can be cured by forcing water in the oposite drection (From the cold tap directly to the hot tap for examle) though be careful that you don't flood the loft!
: If it is a valve seal that is not seating, you need to get either a new valve, a new seal of a valve seating tool.
I, too, am having the same problem. Could you please explain this in greater detail? Specifically, could you explain (or direct me to other resources that do) what a valve seal is, where it's located, and how to replace it.
Thank you very much,
|Replies to this post|