|Posted by hj on November 01, 2001 at 07:49:15:|
|In response to Re: Repairing broken 3 inch cast iron drainage pipe connected to floor drain in a brew pub|
In an installation like that, the brewing process will often deteriorate cast iron pipe to the extent that there is often no bottom to the pipe. I have seldom found a situation like that which did not require extensive pipe replacement. You can switch to plastic using cast-iron to plastic transitions.
: I'm remodeling a brew pub. In the kitchen a large floor drain was not working properly.
: How can I repair this without using cast iron parts?
: Sheezzzz, this is hard work! I'm sore as heck from the jack hammer. HELP!!!
|Replies to this post|
|There are none.|