Posted by hj on January 13, 1999 at 12:19:54:  

In response to Re: Hot Water Heater Upgrade 

You have to go by the pipe's area, and since PI is a constant in the computation, the only criticalmeasurement is the square of the radius. A 3" pipe has an r2 of 2.25 and the r2 of 4" is 4. So if you add 2.25 and 4, youget 6.25, which happens to be the r2 of a 5" pipe. If you put two 4" lines into a 5" pipe, then you have two r2 of 4 which equals 8 trying to go into that same 5" pipe with a r2 of 6.25. When both are operating, the flue will be too small, unless it is rather tall and gets some enhancement from the heat, and the flue gases, (including carbon monoxide), will spill out into the room. Two 4" vents should be combined into a 6" riser. The unit with the larger input will reheat the fastest, and the 75 will usually have a slightly larger input. The other consideration is whether the larger heater will fit into the present space. If the heater location is on the floor, then the new one should be elevated 18" to met code and safety requirements, and if the floor is already at the 18" height, then the larger heater could be tall enough that it is difficult, if not impossible, tomake the necessary connections. : Given my family has doubled, I'm considering replacing my aging 40gal standard gas HW heater : Also, given how rapidly I run out of hot water (5070% more would be nice), should I just bite the : Thanks, Kevin

Replies to this post 
