|Posted by Keith L. on December 31, 1998 at 09:06:53:|
|In response to Re: Low Water Pressure|
The 3/4" pipe would have been ideal. Something you could check is what the pressure differential is set at. You should have a gauge someplace near your pressure switch. Watch the gauge while you run water and seen when the pump kicks on. I don't know what an ideal range is but would guess somewhere around 15 psi. Look on the inside of the pressure switch cover it might be printed there, also, it should tell you which screw to turn to adjust the differential. Good Luck.