|Posted by Dave on December 20, 2001 at 00:15:37:|
|In response to Re: oil furnace won't run without pushing reset button on furnace|
The symptom you're experiencing is that the "flame sensor" is not seeing a flame after a few seconds of operation. Most likely the cause of this failure is that there really is no flame present, thus the safety is doing its job. Oil heaters need regular maintainence, including inspecting the flue, changing the nozzle, changing the fuel filter, check belts if any and blower, replace air filter etc. This isn't that expensive to have done by a pro who has the parts on his or her truck.
There are a myriad of obscure issues with oil heaters of this type, one common source of a tripping safety is a small leak on the inlet side of the piping, which allows bubbles to form just behind the nozzle. These can be a bear to find and fix. Another issue you run into with these is if the piping from the tank to the pump is pinched or too small, the vacum of the pump drawing fluid can cause light oils within the fuel to go from liquid to vapor forming bubbles with the same result as an air leak. You can even get an occasional tank of fuel that's prone to this.
I'd suggest calling a tech. who doesn't mind the smell and has a few years under his or her belt.
|Replies to this post|
|There are none.|