|Posted by Terry Love on November 09, 1998 at 00:50:12:|
|In response to Re: Natural Gas line size|
UPC code, 97,
Gas pressure: 6-7 in. W.C.
Pressure drop 0.5 in. W.C.
30 cubic feet at 250 feet of length for IPS pipe.
: Terry, I have to extend a 1/2" galvi gas line(32') for the installation of a Fire-pit rated at 30,000 btu's. I'm knockin my head aginst the wall try'in to find a copy of the proper chart to size this line correctly. I know it exists in the code book, but I don't have a copy and really would never use it.The line is to be taken frome an existing 1/2" galvi nipple(currently live at 7psi") stubbed out the back of the house, intended for a barbacue hook-up. I'd like to continue with 1/2" but don't know if it's imperitive.
|Replies to this post|