|Posted by Chad Hamann on October 08, 19100 at 23:24:59:|
Hi, I have an old well water system in my basement, it is an old 40 gal. tank. I have been having probs setting the correct "deadspot" for the old FURNAS (now Seimens?) Style "S-48" type 47 pressure switch. Right now, the cut-in is about 16 psi, much too low for the shower, and cut-out is about 40 (now set to 45). HELP PLEASE!
|Replies to this post|
|There are none.|